Purchase this and other courses on trainor.no.
Internal corporate courses
We can hold courses at the customers premises on our own equipment and facilities, or in our specially adapted trailer tailored for practical and real exercises.
When we are holding the course at an external location, it will be required that you have access to an electrical switchboard for practical practice. When practical exercise in live working (AUS) two and two work together. One is AFA and the other performer, change’s role so that everyone gets the job done as AUS.
Everyone must wear long -sleeved protective clothing in flame resistant material and visor and electric insulating gloves. Insulating covering and insulating tools must be available.
After completing the training, the participants shall be able to perform live work on low voltage (AUS).
Personnel performing live work on low voltage installations (AUS).
The course will meet the requirement described in § 16 of the FSE regulation.
§ 16. Live working (AUS) Live working may only be conducted by those with sufficient training in live working, and the work must follow approved methods and applicable work procedures. Before live working may commence, any possible fire and explosions hazards must be eliminated.
Re § 16 Live working For live working, two safety barriers are always required. When working on objects that are located inside the live-working zone, including direct work on live installation parts (known as live working), additional training is required. Training must be documented. The requirement that work must follow relevant work procedures implies the development of a procedure for each work task, based on the selected working method.
Tak, na początku kursu zostanie dostarczony podręcznik do kursu.